|Home||Internet of Things||Aerospace||Apparel||Energy||Defense||Health Care||Logistics||Manufacturing||Retail|
Italian Gas Stations Install Leak-Sensing RFID System
Wolftank is providing a solution that includes nanotron Technologies active RFID tags to send alerts as soon as fuel seepage is detected.
Jul 02, 2012—Wolftank, an Italian petrochemical industry technology firm that manufactures a wide range of products for gas stations and other companies, is providing a gas tank safety solution that includes a radio frequency identification sensor that can detect a potential leak and issue alerts accordingly. The system, which employs RFID technology provided by nanotron Technologies, is currently in use by 50 fuel stations throughout Italy.
Wolftank has 9,000 customers—primarily gas stations—95 percent of which are located in Italy. Most recently, the company has been providing refurbishment services to help gas stations comply with new legislation requiring all gas storage tanks to be double-walled (previous tanks had single walls).
Wolftank provides the cleaning and refurbishment services and equipment necessary to convert single-walled tanks to two walls. In addition, the firm is now offering a solution known as SEF16, with a battery-powered RFID sensor to measure conditions within the underground tank, and to issue an alert in the event that a leak is detected, says Martin Majohr, Wolftank's director of research and development.
With a traditional cabled sensor system, a trench would need to be dug in order to accommodate a cable installed at the tank and traveling back to the station's management system. Using a wireless system renders the cable unnecessary; however, the tag battery may need to be periodically replaced—typically, about once every two years, depending on the conditions around the tank and the frequency of transmissions.
The Wolftank system utilizes an active RFID tag from nanotron that transmits sensor data from an underground tank to a reader installed at the ground surface via a 2.4 GHz transmission complying with the IEEE 802.15.4a standard. The SEF16 tag is inserted into the underground chamber in which the tank is located, at the manhole opening. The tag's sensor measures the pressure between the tank's two walls. If the pressure changes (reaching approximately 300 millibars), the device determines that a leak may have occurred inside the inner storage wall. The tag then transmits an alert to the reader installed at the surface above the tank, with the device forwarding that alert to the gas station's control center, usually located near or in the station office or dedicated kiosk. The tag's typical read range through the ground is 10 meters to 15 meters (33 feet to 49 feet), depending on conditions—some types of soil can be more difficult to transmit through than others.
For stations operating multiple tanks, the distance between a reader and the main station can be large; therefore, repeaters are installed every 200 meters to 300 meters (656 feet to 984 feet). In that case, the reader transmits the tag's sensor data and unique ID number back to the nearest repeater until it reaches the back-end system, where a gateway has a cabled connection to a PC. There, Wolftank's management software interprets the read data, including each tank's unique ID and sensor readings, along with a time and date stamp. That information can then be stored in order to create a record of each tank's sensor readings. Wolftank software typically resides on a user's back-end system, and can share its data with the user's own management software, thereby allowing that company to receive alert messages from its own systems via cell phone, SMS text message or e-mail.
Login and post your comment!
Not a member?
Signup for an account now to access all of the features of RFIDJournal.com!
SEND IT YOUR WAY
RFID JOURNAL EVENTS
ASK THE EXPERTS
Simply enter a question for our experts.
|RFID Journal LIVE!||RFID in Health Care||LIVE! LatAm||LIVE! Brasil||LIVE! Europe||RFID Connect||Virtual Events||RFID Journal Awards||Webinars||Presentations|